« Last post by Jlv on Today at 03:41:56 pm »
Well, I worked it out.
There is power at one of the switch locations coming from the light. I hooked this black wire to the black wire on the GE45607 switch. The white wire fron the GE switch I connected to a neutral in the box (this box is a ganged switch box). The load or blue wire I connected to the wire wire going to the light. The yellow wire from the switch I connected to the red wire going to the light.
At the other switch location, I connected the black and white wires going to the light together. This gets the load connected to the main switch. The striped wire from the Auxiliary switch I connected to a neutral in the box. The yellow wire I connected to the red wire going to the light (this goes to the other box as a trailer).
Be sure to connect the grounds up properly and what do you know, it works.....
I strongly suggest you consult an electrician before you try this. If there is an error here you could very well smoke something.
Bottom line, I believe this problem does indeed have a solution....